Payment & Shipping Terms:
|Rating Voltage:||440VAC/50Hz, 3 Phase 4 Wire, Line Voltage 440V, Phase Voltage 254V||Rated Voltage:||440 VAC|
|Installed Capacity:||Resistive Load: 1200 KW||Control Power:||690 VAC / 50 Hz|
For Diesel Generator Automatic Remote Control 440V 1200K Watt AC Load Bank
AC440-1200kW Automatic Load Bank is mainly used to test the performance of generator. It can provide scientific monitor measure for generating set equipment.
|Rating Voltage/Frequency||440VAC/50Hz, 3 phase 4 wire, line voltage 440V, phase voltage 254V|
|Rated Load Power||Resistive load: 1200kW|
|Installed Capacity||Resistive load: 1200kW|
|Load Step||1,2,2,5,10,10,20,50,100,200,200,200,200, 200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz 3 phase 4 wire (line voltage 380V, phase voltage 220V )|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1600*2600*2000mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
1. Real-time Monitor: through software display main parameter value, such as voltage, current, power, power factor, frequency and time.
2. Security monitoring and control: monitor working state of the load bank by watching software light, when abnormally stop and protect, it can show the reason.
3. Data Collection Interval: the minimum data resolving time is 2s.
4.Data save and query: all the test data is saved in the software, easy to query in the history testing data.
1. for generator power ,the frequency,the voltage,the current,power factor and other generator parameters
2. Because Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce