Payment & Shipping Terms:
1500KW Backup Power Supply Testing Load Bank
AC480-1500kW composed of measurement & control part and load part, mainly including dry type AC load bank, auxiliary control data acquisition system, auto load/unload control system, cooling system etc.
Automatic Load Bank combine the dry type load module and automatic measurement and control module, it can accurately test output power and load capacity of all kinds of generators, offer scientific and high efficiency testing method for large power generator set.
Kaixiang load banks operate at the actual output voltage of medium voltage generators and therefore do not require large step-down transformers, which reduces the overall package size and installation costs. Kaixiang’s quality system is certified to meet ISO9001:2015 standards. Kaixiang AC load banks certified by CE certificate.Our high capacity load banks are exported to more than 20 countries around the globe in a wide variety of applications such as military ships, offshore platforms, data centre, power stations, generator manufacturers and research institutes.Its customers widely distributed in America, Mexico, Netherlands, Australia, Singapore, Israel, Poland, Saudi Arabia, UAE, Egypt, Indonesia, Malaysia,Vietnam, The Philippines, Cambodia, Sudan etc.
|Rating Voltage/Frequency||480VAC 50Hz/60Hz,3phase 4 wire|
|Max Load Power||Resistive Load: 1500kW|
|Load Step||Resistive Load:16 steps; 1,2,2,5,10,10,20,50,100,100,200,200,200,200,200,200kW|
|Load Tolerance(each step)||±5%|
|Display Precision||0.5 class|
|Control Power Supply||External 415VAC, 3phase 4wire 50Hz,|
Load Power Supply Input——Copper bar (star connection)
Control power supply input——Connector bar
|Communication Interface||RS232 and RS485|
|Cooling||Forced air cooling, horizontal air inlet and air outlet|
|Transportation||Hoisting, there are lifting lug in top of case and wheel castors on the bottom|
(Width *Length *Height)
|Operating Environment Parameter|
(1) Temperature Display: display real time temperature.
(2) Measuring meter: display testing data.
(3) Control mode selector switch: [Local] use panel switch manually operated,and point to [Intelligent] can be operated via PC software. Two methods are mutually exclusive modes of operation; please make sure the current operation mode is in accordance with the corresponding mode.
(4) Fan Power Supply: push the button, the indicator lights up, fans will work.
(5) Load Confirm: Master load switch, when the switch is pressed, the yellow indicator lights up, load bank will load/unload according to a preset power loading.
(6) Emergency stop: In case of emergency, press this switch, immediately stop loading. After resolving the emergency problem, clockwise rotary switch, unlock, continues to load.
(7) Power setting switch: totally 16 switches:1,2,2,5,10,10,20,50,100,100,200,200,200,200,200,200kW press the corresponding switches, and press the < Load Confirm >.
(8) Fault: red fault indicator lights up, and with alarm, the load bank will be in protection.
(9)Emergency Stop Indicator: When load bank under emergency stop locked state, the indicator light and send alarm.
(10) Overheat Alarm Indicator:When the unit is overheating, the corresponding warning lights up, load bank gives alarm.
(11) Over-voltage Alarm Indicator:When load bank is under over-voltage protection, the corresponsive light turns on and gives alarm.
(12) Fan Fault Indicator: When load bank is under protection status, corresponding lights on with alarm, from left to right are air volume protection switches of 1-6# fans.
Contact Person: Bruce