Payment & Shipping Terms:
|Name:||ISO IEC CE Electronic Portable Resistive Load Bank With F Insulation||Rated Load Power:||Resistive Load: 200kW|
|Rated Voltage:||400 VAC||Installed Capacity:||Resistive Load: 200kW|
|Load Tolerance(overall):||±3%||Control Power:||220VAC/50Hz,single Phase|
ISO IEC CE Portable Electronic AC Load Bank Single Phase Durable With F Insulation
The system can accurately test output power and load capacity with all kinds of generators. System consists of testing/control and load bank, mainly includes AC load bank, data capture system, auto load/unload control system, heat dissipation device, assist control and PC software. User can control load bank through local control panel, also through software.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 200kW|
|Installed Capacity||Resistive load: 200kW|
|Load Step||1,2,2,5,10,10,20.50.100kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||220VAC/50Hz, single phase|
Load power supply input——terminal block
|Casing Dimensions and Cooling||about 570*530*710mm (length*width*height) Forced air cooling,Horizontal inlet air,Horizontal outlet air|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
Data collection interval: the min saving interval is 2 seconds.
Kaixiang company is in leading position in generator set testing and maintenance industry, besides general functions, its load bank has following unique advantages:
1. Standard Testing Function: The load bank can do stable test, transient test, and realize functions, such as setting, fluctuation, instant load, and instant unload.
2. Super Power Load: high load power density, large capacity of single set, parallel running to finish super power testing, and realize tens of megawatts of power loading.
1. Manufacturers of small gas engines also use load banks to test newly manufactured engines under various mechanical loads.
2.This is accomplished by connecting the engine to the load bank via a device called a dynamometer.
3.engine performance is monitored and, if necessary, adjustments are made to ensure the product performs within intended specifications.
Contact Person: Bruce