Payment & Shipping Terms:
|Rated Power:||100kw||Installed Capacity:||Resistive Load: 100kw|
|Frequency:||50 / 60HZ||Rated Voltage:||400VAC 3 Phase 4 Wire 50hz|
|Load Tolerance (each Step):||±5%||Load Tolerance(overall):||±3%|
|Control Power:||220VAC, 1 Phase 50 Hz,||Name:||3 Phase Load Bank|
100Kw Power With Copper Conductor 3 Ph Ac Load Bank Electric For Generator Power
1. System mainly consists of resistance load, data collecting, control system, cooling device, etc. The system can test output power and load performance of generator sets.
2. The system is a self-developed device used for electricity load testing by Kaixiang Technology. It perfectly combines the dry type load module and measurement and control module, precisely test output power and load performance of kinds of generator set, and realize setting, fluctuation, instant load, instant unload, record wave analysis, and harmonic wave analysis, so to finish all the static parameters and dynamic parameters testing.
|Rating Voltage/Frequency||100Kw at 400VAC, 3 phase 4 wire, 50 Hz,|
|Max Load Power||Resistive load:200kW|
|Load Steps||1kW,2kW,2kW,5kW,10kW,20kW,20kW,50kW, min load step: 1 kW|
|Load Accuracy (each step)||±5%|
|Load Accuracy (overall)||3%|
|Display Precision||0.5 grade|
|Control Power||220VAC, 1 phase 50 Hz,|
Load power supply input——busbar
Control power supply input——three pin socket
|Way of Working||Continuous Work|
|Cooling||Fan forced cooling, horizontal inlet air and vertical outlet cooling|
Load/unload with one key: Either by manual control, or software control, user can preset the power, then press load master button. Load bank will load according to preset power.
Control Pattern: User can choose local control and intelligent control.
Local Control: There are several power steps in panel; user can load/unload by buttons.
Intelligent Control: Through data processing software in PC, user can make automatic load, display, record and manage testing data, form curves and tables, also print them.
Control Pattern interlock: There is control pattern switch, when choose one control pattern, the other pattern is invalid to avoid the clash.
1. Ups system testing
2. Load optimization in prime power applications
3. Factory testing of turbines
4. factory testing of engine generator sets
5. To reducewet stacking problems
6. Periodic excercising of stand-by engine generator sets
Contact Person: Bruce