Payment & Shipping Terms:
|Casing Dimensions And Cooling:||About 4000*2350*2591mm (length*width*height) Forced Air Cooling，Horizontal Inlet Air，Vertical Cooling||Transportation:||Hoisting, There Are Lifting Lug In Top Of Casing|
|Casing Color:||Grey（RAL7035）||Ambient Temperature:||-10℃～+50℃|
|Voltage Range:||AC400v 50hz ±10%||Display Precision:||0.5 Class|
1000KVAConnection Box Load Bank Cabinet Grey Casing Color For Generator Testing
The system can accurately test output power and load capacity with all kinds of generators. System consists of testing/control and load bank, mainly includes AC load bank, data capture system, auto load/unload control system, heat dissipation device, assist control and PC software. User can control load bank through local control panel, also through software.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Voltage range||400v 50hz ±10%|
|Max Rated power|
Apparent Power: 1000kVA
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||AC380VAC/50Hz,3 phase 4 wire|
Load power supply input——Copper bar (star coupling)
|Casing Dimensions and Cooling||about 4000*2350*2591mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
Communication type: through RS232, RS485
Load mode: manual load or automatic load.
Manual load: input power and power factor.
Automatic load: User can set several periods of power and time, and in turn of 0%→25%→50%→75%→100%, etc preset order to make automatic load testing.
Motor manufacturing: The load bank is an ideal test equipment for generator power ,the frequency,the voltage,the current,power factor and other generator parameters.Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce