Payment & Shipping Terms:
|Casing Dimensions And Cooling:||About 4000*2350*2591mm (length*width*height) Forced Air Cooling，Horizontal Inlet Air，Vertical Cooling||Transportation:||Hoisting, There Are Lifting Lug In Top Of Casing|
|Casing Color:||Grey（RAL7035）||Ambient Temperature:||-10℃～+50℃|
|Voltage Range:||AC400v 50hz ±10%||Display Precision:||0.5 Class|
Genset Load Bank 1000KVAConnection Box / Load Bank Cabinet Grey Casing Color
According to the special requirements of users on site, in the agreement the technical standards of AC500-1000kVA-RL Intelligent Load Bank (hereinafter referred to as "system") and its accessories are proposed including their function, performance, usage, structure, installation and test to provide users with a high efficient and reliable choice, in order to meet the need for generator load test.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Voltage range||400v 50hz ±10%|
|Max Rated power|
Apparent Power: 1000kVA
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||AC380VAC/50Hz,3 phase 4 wire|
Load power supply input——Copper bar (star coupling)
|Casing Dimensions and Cooling||about 4000*2350*2591mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
User could load any power within rated power, can test stable state three-phase voltage, current, active power, apparent power, power factor, frequency, running time of generating set.
Whether load/unload by manual control panel or by PC software control, user can pre-set the power then press the master load button.
Control mode: user can choose local manual control or Intelligent control(PC control)
Motor manufacturing: The load bank is an ideal test equipment for generator power ,the frequency,the voltage,the current,power factor and other generator parameters.Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce