Payment & Shipping Terms:
|Resistive Load:||500KW||Load Tolerance:||±3%|
|Control Power:||380VAC/50Hz, 3 Phase 4 Line||Insulation:||F|
Over Heat Protection Variable Resistive Electrical 500Kw Load Bank
The system can accurately test the output power and load capacity of various generator sets.The system consists of two parts of measurement and loading, including AC load bank, data acquisition system, automatic load and drop control system, cooling device, auxiliary control,PC software,and so on.The user can freely select local control or software control to operate the load bank.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 500kW|
|Installed Capacity||Resistive load: 500kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1550*1250*1680mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
User could load any power within rated power, can test stable state three-phase voltage, current, active power, apparent power, power factor, frequency, running time of generating set.
Whether load/unload by manual control panel or by PC software control, user can pre-set the power then press the master load button.
1.Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units
2.generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance.
3.During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce