Payment & Shipping Terms:
|Resistive Load:||500KW||Load Tolerance:||±3%|
|Control Power:||380VAC/50Hz, 3 Phase 4 Line||Insulation:||F|
Safety Monitoring Variable 500KW Electrical Load Bank Continuous Working
1.Local Control: There is local control panel with several power steps; user can load/unload by button.
2.Intelligent Control: Through data processing software in PC, user can make automatic load, to display, record and manage the testing data, to form curves, tables, also to print them.
3.Control Pattern interlock:there is control pattern switch, when choose one control pattern, operation of other pattern is invalid, avoid the clash.
4.Local meter display data: local meter can display 3 phases voltage, current, active power, frequency and so on.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 500kW|
|Installed Capacity||Resistive load: 500kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1550*1250*1680mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
Communication type: through RS232, RS485
Load mode: manual load or automatic load.
Manual load: input power and power factor.
Automatic load: User can set several periods of power and time, and in turn of 0%→25%→50%→75%→100%, etc preset order to make automatic load testing.
Parallel testing: when several load banks parallel working, parameters of each load bank can be displayed and recorded, so do the final parameters of paralleling working.
Real-time parameter: Current, voltage, power, power factor, frequency, time, etc could be displayed by software.
1.Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units
2.generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance.
3.During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce