Payment & Shipping Terms:
|Resistive Load:||3000 KW||Display Precision:||0.5 Class|
|Load Step:||10、20、20、50、100、200kW*14, Total 19 Steps, Min Step Load: 10kW.||Rating Voltage/Frequency:||400VAC 50/60Hz, 3 Phase 4 Wire, Line Voltage 400V, Phase Voltage 230V|
For Generator Waterproof Within Rated Power Remote Control Dummy Load bank
The system is made up of two parts of measurement and control and load, mainly including the tank dry type ac load, automatic data acquisition system, automatically loading and unloading control system, the cooling device, auxiliary control, box and PC software and so on.
|Rating Voltage/Frequency||400VAC 50/60Hz, 3 phase 4 wire, line voltage 400V, phase voltage 230V|
|Rated Load Power||Resistive load: 3000kW|
|Installed Capacity||Resistive load: 3000kW|
|Load Step||10,20,20,50,100,200kW*14, total 19 steps, min step load: 10kW.|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC 50Hz 3 phase 4 wire (Line voltage 380V, phase voltage 220VAC)|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||
Forced air cooling,Horizontal inlet air,Vertical cooling
6058*2438*2591mm (L*W*H) 20’GP container type.
|Transportation||Hoisting, there are lifting lug in top of casing|
1. Users can set adjustable load power within rated power.
2. Current, voltage, frequency, power factor, and active power, reactive power, and apparent power can be displayed.
3. With software programmable control, graphs of current, voltage, frequency, power factor, power can be displayed, saved and printed.
1. for generator power ,the frequency,the voltage,the current,power factor and other generator parameters
2. Because Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce