Payment & Shipping Terms:
|Rating Voltage:||400VAC/50Hz, 3 Phase 4 Wir||Rated Load Power:||Resistive Load: 100kW|
|Rated Voltage:||400 VAC||Installed Capacity:||Resistive Load: 100kW|
|Load Tolerance(overall):||±3%||Control Power:||220VAC/50Hz,single Phase|
Professional Design And Produce 100kw Generator Resistive Load Bank
1. load bank can accurately test the output power and load capacity of various generator sets
2.the system consists of two parts of measurement and loading, including AC load bank, data acquisition system, automatic load and drop control system, cooling device, auxiliary control,PC software,and so on.
3.The user can freely select local control or software control to operate the load bank.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 100kW|
|Installed Capacity||Resistive load: 100kW|
|Load Step||1,2,2,5,10,10,20,50kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||220VAC/50Hz, single phase|
Load power supply input——terminal block
|Casing Dimensions and Cooling||about 860*570*710mm (length*width*height) Forced air cooling,Horizontal inlet air,Horizontal outlet air|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
The system can be used with a computer to realize the intelligent control, automatically completing the special test to all electrical parameters of generating set and generating tables, graphs, and supporting the print, comprehensively from the cumbersome manual operation to provide scientific and efficient detection means for the power generating sets.
Motor manufacturing: The load bank is an ideal test equipment for generator power ,the frequency,the voltage,the current,power factor and other generator parameters.Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load
Contact Person: Bruce