Payment & Shipping Terms:
|Resistive Load:||500KW||Load Tolerance:||±3%|
|Control Power:||380VAC/50Hz, 3 Phase 4 Line||Insulation:||F|
|Altitude:||≤1500 Meter||Name:||Electrical Load Bank|
Plastic Housing And 500Kw Load Bank 3 Phase For Backup Power Supply Generator
Automatic AC load bank main used to test the capability and aging degree for high-power ups on-line, inverter, switch power and diesel generator set for electric power, telecom department and manufacturer. It can ensure the reliability of constant power charge that adopts uniformly stepped power input, energy consumption work model and forced air-cooling model. It is of high power density, no red hot phenomenon and automatic protection function overheated. It can’t be overheated and broken when the fans stop working. The complete machine can be operated simply and maintain convenient that adopts module design. It can test voltage and current according to client’s request, and provide scientific test measures for high-power AC equipment.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 500kW|
|Installed Capacity||Resistive load: 500kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1550*1250*1680mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
Communication type: through RS232, RS485
Load mode: manual load or automatic load.
Manual load: input power and power factor.
Automatic load: User can set several periods of power and time, and in turn of 0%→25%→50%→75%→100%, etc preset order to make automatic load testing.
Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units. When the generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance. During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce