Payment & Shipping Terms:
|Resistive Load:||1440 KW||Load Tolerance:||±3%|
|Control Power:||380VAC/50Hz,||Load Step:||F1,2,2,5,10,20,20,50,100,100,200,200,200,200,200,200, 200,200,200,200,200,200,200,200,200,200,200,200,200,200,200kw,|
|Altitude:||≤2500 Meter||Rating Voltage/Frequency:||504V 60HZ|
Ocean Engineering Dummy Electrical Load Bank 1440KW Generator Test
The system consists of 1 sets of 1440kw load bank. The system is made up of two parts of measurement and control and load, mainly including the dry type ac load, automatic data acquisition system, automatically loading and unloading control system, the cooling device, auxiliary control, remote control box and PC software and so on.
|Rating Voltage/Frequency||480VAC/60Hz, 3 phase 4 wire, line|
|Max Rated voltage||504V 60HZ|
A Phase 10,20,20,,20,50kw
B phase 10,20,20,,20,50kw
C phase 10,20,20,,20,50kw
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Casing Dimensions and Cooling||about 2800*1900*2400mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
1. Manual load: input power and power factor.
2. Automatic load: User can set several periods of power and time, and in turn of 0%→25%→50%→75%→100%, etc preset order to make automatic load testing.
3. Parallel testing: when several load banks parallel working, parameters of each load bank can be displayed and recorded, so do the final parameters of paralleling working.
4. Real-time parameter: Current, voltage, power, power factor, frequency, time, etc could be displayed by software.
Load banks may be installed in a diesel powered generator set to apply the additional load required to ensure the engine fully consumes the fuel in the combustion process. If a diesel engine is not operated under adequate load, unconsumed fuel will collect in the engine’s exhaust stack and form an oily coating.
Contact Person: Bruce