Payment & Shipping Terms:
|Rated Power:||200kw||Installed Capacity:||Resistive Load: 200kW|
|Frequency:||50 / 60HZ||Rated Voltage:||400VAC 3 Phase 4 Wire 50hz|
|Load Tolerance (each Step):||±5%||Load Tolerance(overall):||±3%|
|Control Power:||220VAC, 1 Phase 50 Hz,||Insulation:||F|
LCD display Intelligent 400V 200Kw Dummy Load Bank For Generator Testing
1.our load bank an accurately test output power and load capacity with all kinds of generators.
2.System consists of testing/control and load bank, mainly includes AC load bank, data capture system, auto load/unload control system, heat dissipation device, assist control and PC software.
3.User can control load bank through local control panel, also through software
|Rating Voltage/Frequency||200Kw at 400VAC, 3 phase 4 wire, 50 Hz,|
|Max Load Power||Resistive load:200kW|
|Load Steps||1kW,2kW,2kW,5kW,10kW,20kW,20kW,50kW, 100kW,min load step: 1 kW|
|Load Accuracy (each step)||±5%|
|Load Accuracy (overall)||3%|
|Display Precision||0.5 grade|
|Control Power||220VAC, 1 phase 50 Hz,|
Load power supply input——busbar
Control power supply input——three pin socket
|Way of Working||Continuous Work|
|Cooling||Fan forced cooling, horizontal inlet air and vertical outlet cooling|
About resistor alloy, we use nickel-chromium alloy(NiCr6023) which can withstand high temperature (Max operation temperature at 1,300℃), be of small temperature drift (5*10-5/℃) and steady electrical performance.
1.Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units
2.generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance.
3.During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce