Payment & Shipping Terms:
|Rating Voltage:||380VAC/50Hz, 3 Phase 4 Wire, Line Voltage 380V, Phase Voltage 220V||Rated Load Power:||Resistive Load: 1000kW|
|Rated Voltage:||380 VAC||Installed Capacity:||Resistive Load: 1010kW|
|Load Tolerance(overall):||±3%||Control Power:||400VAC/50Hz, 3 Phase 4 Wire, 230V 1-phase|
Anti Corrosion Materials Professional Produce AC Load Bank For Generator Testing
1. our load bank an accurately test output power and load capacity with all kinds of generators.
2. System consists of testing/control and load bank, mainly includes AC load bank, data capture system, auto load/unload control system, heat dissipation device, assist control and PC software.
3. User can control load bank through local control panel, also through software
|Rating Voltage/Frequency||380VAC/50Hz, 3 phase 4 wire, line voltage 380V, phase voltage 220V|
|Rated Load Power||Resistive load: 1000kW|
|Installed Capacity||Resistive load: 1010kW|
|Load Step||1,2,2,5,10,20,20,50,100,200,200,200,200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||400VAC/50Hz, 3 phase 4 wire, 230V 1-phase|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Casing Dimensions and Cooling||about 1600*2400*2100mm (length*width*height) Forced air cooling,Horizontal inlet air,Horizontal outlet air|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
User could load any power within rated power, can test stable state three-phase voltage, current, active power, apparent power, power factor, frequency, running time of generating set.
Whether load/unload by manual control panel or by PC software control, user can pre-set the power then press the master load button.
1.Manufacturers of small gas engines also use load banks to test newly manufactured engines under various mechanical loads.
2.This is accomplished by connecting the engine to the load bank via a device called a dynamometer.
3.engine performance is monitored and, if necessary, adjustments are made to ensure the product performs within intended specifications.
Contact Person: Bruce