Payment & Shipping Terms:
|Rating Voltage:||400VAC/50Hz, 3 Phase 4 Wire||Rated Load Power:||Resistive Load: 1000kW|
|Rated Voltage:||400 VAC||Installed Capacity:||Resistive Load: 1000kW|
|Load Tolerance(overall):||±3%||Control Power:||380VAC/50Hz, 3 Phase 4 Wire, 230V 1-phase|
AC Dummy 1000KW Load Bank For Generator Testing China Brand Load Bank
Resistance/inductance/capacity Automatic load bank
Automatic AC load bank main used to test the capability and aging degree for high-power ups on-line, inverter, switch power and diesel generator set for electric power, telecom department and manufacturer. It can ensure the reliability of constant power charge that adopts uniformly stepped power input, energy consumption work model and forced air-cooling model. It is of high power density, no red hot phenomenon and automatic protection function overheated. It can’t be overheated and broken when the fans stop working. The complete machine can be operated simply and maintain convenient that adopts module design. It can test voltage and current according to client’s request, and provide scientific test measures for high-power AC equipment.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 1000kW|
|Installed Capacity||Resistive load: 1000kW|
|Load Step||1,2,2,5,10,20,20,50,100,200,200,200,200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Casing Dimensions and Cooling||about 1680*2400*1440mm (length*width*height) Forced air cooling,Horizontal inlet air,Horizontal outlet air|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
About resistor alloy, we use nickel-chromium alloy(NiCr6023) which can withstand high temperature (Max operation temperature at 1,300℃), be of small temperature drift (5*10-5/℃) and steady electrical performance.
1.Manufacturers of small gas engines also use load banks to test newly manufactured engines under various mechanical loads.
2.This is accomplished by connecting the engine to the load bank via a device called a dynamometer.
3.engine performance is monitored and, if necessary, adjustments are made to ensure the product performs within intended specifications.
Contact Person: Bruce