Payment & Shipping Terms:
|Resistive Load:||2000 KW||Display Precision:||0.5 Class|
|Control Power:||Resistive Load: 2000kW||Rating Voltage/Frequency:||400VAC/50Hz, 3 Phase 4 Wire, Line Voltage 400V, Phase Voltage 230V|
|Load Resolution:||Resistive:100.200.400.500.500.800kw Inductive:220.127.116.11.250.400kvar Capacitive:18.104.22.168.250.400kvar||Weight:||4000kg|
Testing on Generator Sets 400V 2000kw Dummy Generator Load Bank
1. AC Load Bank offers the most robust, high-capacity designs in the industry.
2. It is setting the standard with intelligent operator controls, safety indication layouts, adjustable load step resolution, and lightweight designs.
3. AC Load Bank is the perfect solution for regularly scheduled maintenance testing and commissioning of mission-critical standby emergency power systems.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire, line voltage 400V, phase voltage 230V|
|Rated Load Power||Resistive load: 2000kW|
|Installed Capacity||Resistive load: 2000kW|
|Load Step||1,2,2,5,10,10,20,50,100,200kW*9, total 18 steps, min step load: 1kW for each set of 2000kW load bank.|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||3 phase 4 wire 380VAC/50Hz|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||
Forced air cooling,Horizontal inlet air,Vertical cooling
about 6058*2438*2591mm (L*W*H) for 1 set of 2000kW load bank
|Transportation||Hoisting, there are lifting lug in top of casing|
1. The complete machine is of resistance breaking automatic overheated adopts new power consumption component.
2. AC load bank is of all kinds of specifications and series, and include resistance, inductive and capacitive load.
3. It ‘s of machine combination function.
Motor manufacturing: The load bank is an ideal test equipment for generator power ,the frequency,the voltage,the current,power factor and other generator parameters.Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce