Payment & Shipping Terms:
|Resistive Load:||2000KW||Load Tolerance:||±3%|
|Control Power:||380VAC/50Hz, 3 Phase 4 Line, 220V 1-phase||Insulation:||F|
New High Accuracy Top Quality Auto 400V 2000kw Electrical Resistive Load Bank
1. load bank can accurately test the output power and load capacity of various generator sets
2.the system consists of two parts of measurement and loading, including AC load bank, data acquisition system, automatic load and drop control system, cooling device, auxiliary control,PC software,and so on.
3.The user can freely select local control or software control to operate the load bank.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 2000kW|
|Installed Capacity||Resistive load: 2000kW|
|Load Step||1,2,2,5,10,10,20,50,100,100,200kW*9, total 19 steps,|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 4000*2350*2591mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
User could load any power within rated power, can test stable state three-phase voltage, current, active power, apparent power, power factor, frequency, running time of generating set.
Whether load/unload by manual control panel or by PC software control, user can pre-set the power then press the master load button.
Control mode: user can choose local manual control or Intelligent control(PC control)
Large generator system testing in ocean engineering, drilling facilities,ship construction
Factory testing for generator, static voltage characteristic test, speed characteristic test;
Marine generator overload protection test,parallel operation test,reverse power and reverse current protection test
Assist shipyard in mooring test,sea trial test
Assist with the acceptance of the vessel generator test
Eliminate the carbon deposition of generator
Contact Person: Bruce