Payment & Shipping Terms:
|Resistive Load:||2000 KW||PF:||1|
|Load Tolerance:||±3%||Display Precision:||0.5 Class|
|Altitude:||≤2500 Meter||Relative Humidity:||≤95%|
6.6KV 2000Kw Full Auto Generator Load Bank Testing On Generator Sets
1. Communication Mode:RS485/ USB or RS232 interface for communication.
2. Load Mode: manual load or automatic load
3. Manual Load: input power and power factor, and load according to the preset value.
4. Automatic Load: set several load stages and duration, then complete the process according this stages automatically. 0%- 25%,- 50%,- 75%, -100%
|Rating Voltage/Frequency||10.5kV/50Hz, 3 phase 3 wire|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
1. Real-time Monitor: through software display main parameter value, such as voltage, current, power, power factor, frequency and time.
2. Security monitoring and control: monitor working state of the load bank by watching software light, when abnormally stop and protect, it can show the reason.
3. Collection Interval: the minimum data resolving time is 2s.
1. for generator power ,the frequency,the voltage,the current,power factor and other generator parameters
2. Because Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce