Payment & Shipping Terms:
|Name:||Variable Resistive Load Bank||Model Number:||AC400V-1500KW|
|Frequency:||50 / 60 HZ||Rated Power:||1500 KW|
|Rated Voltage:||400 VAC||Rated Current:||Depend|
|Cooling:||Forced Air Cooling||CasingColor:||Grey (RAL7035) Or As Request|
AC Variable Resistive 400v 1500kw Resistive Load Bank For Testing Generators UPS
1. Load testing: load power that not beyond the rated power, testing and display stable state 3 phases voltage, current, active power, frequency, working time, etc of generator sets.
2. Load/unload with one key:Either by manual control or software control, user can preset the power, then press load master button. Load bank loaded according to preset power to avoid load fluctuation during the power changing.
3. Control Pattern: user can choose local control and intelligent control.
4. Local Control: There is local control panel with several power steps; user can load/unload by button.
|Rating Voltage/Frequency||400VAC 50Hz/60Hz,3phase 4 wire|
|Max Load Power||Resistive Load: 1500kW|
Resistive Load:16 steps
|Load Tolerance(each step)||±5%|
|Display Precision||0.5 class|
|Control Power Supply||External 415VAC, 3phase 4wire 50Hz|
Load Power Supply Input——Copper bar (star connection)
|Communication Interface||RS232 and RS485|
|Cooling||Forced air cooling, horizontal air inlet and air outlet|
|Transportation||Hoisting, there are lifting lug in top of case and wheel castors on the bottom|
Communication type: through RS232, RS485
Load mode: manual load or automatic load.
Manual load: input power and power factor.
Automatic load: User can set several periods of power and time, and in turn of 0%→25%→50%→75%→100%, etc preset order to make automatic load testing.
UPS inspection and maintenance
Ship battery charging/discharging system testing
The acceptance of new system and testing of servicing equipment
Generators installed in the field must be periodically tested and exercised to ensure that it will operate as intended when a power outage actually occurs. Service groups use load banks to apply a load that mimics the load of the facility the generator is protecting. Any problems with the generator can then be identified and rectified in a non-critical environment.
Contact Person: Bruce