Payment & Shipping Terms:
|Rating Voltage:||380VAC/50Hz, 3 Phase 4 Wire, Line Voltage 380V, Phase Voltage 220V||Rated Voltage:||400 VAC|
|Installed Capacity:||Resistive Load: 1010kW||Control Power:||400VAC/50Hz, 3 Phase 4 Wire, 230V 1-phase|
|Size:||1600*2400*2100mm||Load Step:||1、2、2、5、10、20、20、50、100、200、200、200、200kW, Min Step Load: 1kW|
|Transportation:||Hoisting, There Are Lifting Lug In Top Of Casing||Relative Humidity:||≤95%|
For Diesel Generator 400V 1000K Watt AC Load Bank For Generator Testing
The system consists of 1 sets of 1000 kw load bank. The system is made up of two parts of measurement and control and load, mainly including the dry type ac load, automatic data acquisition system, automatically loading and unloading control system, the cooling device, auxiliary control, remote control box and PC software and so on.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire, line voltage 380V, phase voltage 230V|
|Rated Load Power||Resistive load: 1000kW|
|Installed Capacity||Resistive load: 1010kW|
|Load Step||1,2,2,5,10,20,20,50,100,200,200,200,200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||400VAC/50Hz, 3 phase 4 wire, 230V 1-phase|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1600*2400*2100mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
1. Communication pattern: Intelligent control use photoelectric isolated RS485 interface connect to PC, with great anti-interference performance to make system control stable.
2. Load pattern: Manual Load or Automatic Load.
3. Manual Load: Input power, system will load according to preset power.
4. Automatic load: User can preset power and length of working time of several load periods, as per 0%→25%→50%→75%→100% or 110% to make testing
1. Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units
2. generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance.
3. During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce