Payment & Shipping Terms:
|Rated Power:||500 KW||Installed Capacity:||Resistive Load: 500kW|
|Frequency:||50/60HZ||Rated Voltage:||400 VAC|
|Rated Current:||Depend||Size:||About 1460*1980*1800mm (length*width*height)|
Custome Design Professional 400v 500kw AC Load Bank Capacity Tester
1. Automatic AC load bank main used to test the capability and aging degree for high-power ups on-line, inverter, switch power and diesel generator set for electric power, telecom department and manufacturer.
2. It can ensure the reliability of constant power charge that adopts uniformly stepped power input, energy consumption work model and forced air-cooling model.
3. It is of high power density, no red hot phenomenon and automatic protection function overheated.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire, line voltage 400V, phase voltage 230V|
|Rated Power||Resistive load:500kW|
|Installed Capacity||Resistive load: 500kW|
|Load Step||1,2,2,5,10,10,20,50,100,100,200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||Single voltage 220VAC 50Hz|
Load power supply input——Copper bar (star coupling “Y”)
Control power supply input——Connector-bar
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1460*1980*1800mm (length*width*height) Forced air cooling,Horizontal inlet air and vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing, also the wheel casters can be provided|
|Casing Color||Grey(RAL7035)or as you required|
|Data processing software||Kaixiang(self-developed)|
1. Real-time Monitor: through software display main parameter value, such as voltage, current, power, power factor, frequency and time.
2. Security monitoring and control: monitor working state of the load bank by watching software light, when abnormally stop and protect, it can show the reason.
3. Data Collection Interval: the minimum data resolving time is 2s.
4. Data save and query: all the test data is saved in the software, easy to query in the history testing data.
1. Assist with the acceptance of the vessel generator test
2. Eliminate the carbon deposition of generator
3. As the generator loading system
4. Periodic running test for standby generator
Contact Person: Bruce