Payment & Shipping Terms:
|Rating Voltage:||380VAC/50Hz, 3 Phase 4 Wir||Rated Load Power:||Resistive Load: 500kW|
|Rated Voltage:||380 VAC||Installed Capacity:||Resistive Load: 500kW|
|Load Tolerance(overall):||±3%||Control Power:||400VAC/50Hz, 3 Phase 4 Wire|
Automatic High Capacity Portable Resistive AC 500kw Load Bank Accurate
1. load bank can accurately test the output power and load capacity of various generator sets
2.the system consists of two parts of measurement and loading, including AC load bank, data acquisition system, automatic load and drop control system, cooling device, auxiliary control,PC software,and so on.
3.The user can freely select local control or software control to operate the load bank.
|Rating Voltage/Frequency||380VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 500kW|
|Installed Capacity||Resistive load: 500kW|
|Load Step||1,2,2,5,10,10,20,50,100,100,200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||400VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Casing Dimensions and Cooling||about 1550*1250*1680mm (length*width*height) Forced air cooling,Horizontal inlet air,Horizontal outlet air|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
1.Stable Running: with the latest generation control module as the core, a sharp rise in system response speed and anti-interference performance, avoid function failure in complex electrical environment, and ensure system running stably and reliably.
2.New Load Bank Technology: using the international advanced AC load bank technology, overcome the old water bank defects, such as bear bumpy, unable to use when go to sea, realize Mooring Trial and Sea Trail, and simulate the real working condition of generator running.
1.Manufacturers of small gas engines also use load banks to test newly manufactured engines under various mechanical loads.
2.This is accomplished by connecting the engine to the load bank via a device called a dynamometer.
3.engine performance is monitored and, if necessary, adjustments are made to ensure the product performs within intended specifications.
Contact Person: Bruce