Payment & Shipping Terms:
|Rating Voltage:||400VAC/50Hz, 3 Phase 4 Wire||Rated Load Power:||Resistive Load: 1000kW|
|Rated Voltage:||400 VAC||Installed Capacity:||Resistive Load: 1000kW|
|Load Tolerance(overall):||±3%||Control Power:||380VAC/50Hz, 3 Phase 4 Wire, 230V 1-phase|
1000KW AC 3 Phase Variable Resistive Dummy Load Bank for Generator Testing
Automatic AC load bank main used to test the capability and aging degree for high-power ups on-line, inverter, switch power and diesel generator set for electric power, telecom department and manufacturer. It can ensure the reliability of constant power charge that adopts uniformly stepped power input, energy consumption work model and forced air-cooling model. It is of high power density, no red hot phenomenon and automatic protection function overheated. It can’t be overheated and broken when the fans stop working. The complete machine can be operated simply and maintain convenient that adopts module design. It can test voltage and current according to client’s request, and provide scientific test measures for high-power AC equipment.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 1000kW|
|Installed Capacity||Resistive load: 1000kW|
|Load Step||1,2,2,5,10,20,20,50,100,200,200,200,200kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Casing Dimensions and Cooling||about 1680*2400*1440mm (length*width*height) Forced air cooling,Horizontal inlet air,Horizontal outlet air|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
1. Fan protection: Machine could not do load testing before working power of fan is on.
2. The machine will unload and give alarm when any fan is abnormal or with insufficient air volume, etc.
3. When control power cable in wrong connections, 3 phase fans can also work in good conditions.
4. Protection button: there are some protection buttons can be switched off when false alarm or for special requirements.
1. Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units
2. generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance.
3. During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce