Payment & Shipping Terms:
|Rating Voltage/frequency:||3 Phase 4 Wire, Line Voltage 400V,||Max Load Power:||440 KW|
|Control Source:||400VAC 50Hz||Wire Connection:||Control Power Input——busbar|
|Dimensions:||About 1500mm×1530mm×1700mm L×W×H||Weight:||About 750kgs|
400Kw Resistive Load Bank color Choose For Generator Testing
AC400-400kW Intelligent Load Bank is mainly used to test the performance of generator. It can provide scientific monitor measure for generating set equipment.
|Rating Voltage/Frequency||3 phase 4 wire, line voltage 400V,|
|Rated Power||Resistive load: 440kW|
|Installed Capacity||Resistive load: 440kW|
|Load Step||1,2,2,5,10,10,10,20,20,20,50,100,200kW, min step load: 1kW|
|Load Tolerance(each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC 50Hz|
Load power supply input——Copper bar (star coupling “Y”)
Control power supply input——Connector-bar
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1500mm×1530mm×1700mm
(length*width*height) Forced air cooling,Horizontal inlet air and vertical cooling
|Transportation||Hoisting, there are lifting lug in top of casing, also the wheel casters can be provided|
|Casing Color||Grey(RAL7035)or as you required|
|Data processing software||Kaixiang(self-developed)|
Our load bank of Communication Mode:RS485/ USB or RS232 interface for communication.
this load Mode has manual load or automatic load two ways for choose .
Manual Load: input power and power factor, and load according to the preset value.
Automatic Load: set several load stages and duration, then complete the process according this stages automatically. 0%- 25%,- 50%,- 75%, -100%
Manufacturers of standby power generators commonly use load banks to test and tune newly assembled units. When the generator has been set up in a test cell within the factory, a test engineer uses the load bank to apply a discrete, selectable electrical load to the generator and measure the response stability and endurance. During this process, the test engineer calibrates and adjusts the generator performance to ensure it meets the intended product specifications and tolerances.
Contact Person: Bruce