Payment & Shipping Terms:
|Resistive Load:||500KW||Load Tolerance:||±3%|
|Control Power:||380VAC/50Hz, 3 Phase 4 Line||Insulation:||F|
|Altitude:||≤1500 Meter||Name:||Generator Load Bank Test|
500Kw Load Bank 3 Phase For Backup Power Supply Generator UPS Transformer
1. Automatic AC load bank main used to test the capability and aging degree for high-power ups on-line, inverter, switch power and diesel generator set for electric power, telecom department and manufacturer.
2. It can ensure the reliability of constant power charge that adopts uniformly stepped power input, energy consumption work model and forced air-cooling model.
3. It is of high power density, no red hot phenomenon and automatic protection function overheated.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 500kW|
|Installed Capacity||Resistive load: 500kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||380VAC/50Hz, 3 phase 4 wire,|
Load power supply input——Copper bar (star coupling)
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1550*1250*1680mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
User could load any power within rated power, can test stable state three-phase voltage, current, active power, apparent power, power factor, frequency, running time of generating set.
Whether load/unload by manual control panel or by PC software control, user can pre-set the power then press the master load button.
Control mode: user can choose local manual control or Intelligent control(PC control)
Manufacturers of small gas engines also use load banks to test newly manufactured engines under various mechanical loads. This is accomplished by connecting the engine to the load bank via a device called a dynamometer. Again, engine performance is monitored and, if necessary, adjustments are made to ensure the product performs within intended specifications.
Contact Person: Bruce