Payment & Shipping Terms:
|Rating Voltage:||400VAC/50Hz, 3 Phase 4 Wire,||Rated Voltage:||440 VAC|
|Installed Capacity:||Resistive Load: 200kW||Control Power:||220VAC / 50 Hz 1 Phase|
200KW Resistive Load Bank Calculation Continuous Working For Generator
It offers the most robust, high-capacity designs in the industry. It is setting the standard with intelligent operator controls, safety indication layouts, adjustable load step resolution, and lightweight designs. It is the perfect solution for regularly scheduled maintenance testing and commissioning of mission-critical standby emergency power systems.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Rated Load Power||Resistive load: 200kW|
|Installed Capacity||Resistive load: 200kW|
|Load Step||1,2,2,5,10,10,20,50,100kW, min step load: 1kW|
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
|Control Power||220VAC/50Hz 1 phase|
Load power supply input——Copper bar (star coupling)
|Way of Working||Continuous Working|
|Casing Dimensions and Cooling||about 1450*900*870mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
Communication Mode: using photoelectric isolated RS485 communication serial port connect to PC, and with great anti-interference performance to make system control stable. Through converts like USB or RS232 realize communication protocol conversion.
Generators installed in the field must be periodically tested and exercised to ensure that it will operate as intended when a power outage actually occurs. Service groups use load banks to apply a load that mimics the load of the facility the generator is protecting. Any problems with the generator can then be identified and rectified in a non-critical environment.
Contact Person: Bruce