Payment & Shipping Terms:
|Resistive Load:||14700KW||Display Precision:||0.5 Class|
|Load Step:||Resistive Load: 30 Steps, 200kW×1, 500KW×29, Min Step Load: 500KW||Rating Voltage/Frequency:||11kVAC/60Hz, 3 Phase 4 Wire|
Testing on Generator Sets 11VAC 14700kw Dummy Generator Load Bank
The system can accurately test the output power and load capacity of various generator sets.The system consists of two parts of measurement and loading, including AC load bank, data acquisition system, automatic load and drop control system, cooling device, auxiliary control,PC software,and so on.The user can freely select local control or software control to operate the load bank.
|Rating Voltage/Frequency||11kVAC/60Hz, 3 phase 4 wire|
|Rated Load Power||Resistive load: 14700kW|
|Installed Capacity||Resistive load: 14700kW|
|Load Step||Resistive load: 30 steps, 200kW×1, 500KW×29, min step load: 500KW|
|Load Tolerance(each step)||±5%|
|Display Precision||0.5 class|
|Control Power||3 phase 4 wire 380V/50Hz|
Load power supply input——Copper bar (star coupling)
|Communication Interface||RS485, RS232|
|Max Protection Grade||IP54|
|Way of Working||Continuous Work|
|Cooling||Forced air cooling,Horizontal inlet air,Vertical cooling|
|Casing Structure||Container, with a ladder, air inlet and outlet with mesh enclosure and protection door|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Casing Color||Grey(RAL7035)or as per customer’s requirement|
|Dimension||3 container of 6058 mm×2438mm×2591mm(length*width*height)|
1. High Efficiency Data Management: display real-time testing data, generate form, curve graph or report automatically, also can put data into storage. According to generator set No. set up testing file, support to query at any time, and improve data management efficiency.
2. Comprehensive Protection Function: multiple protection, like over temperature, smoke. When in danger, automatically terminate the test and give alarm to protect safety of personnel and equipment.
3. Stable Running: with the latest generation control module as the core, a sharp rise in system response speed and anti-interference performance, avoid function failure in complex electrical environment, and ensure system running stably and reliably.
Manufacturers of small gas engines also use load banks to test newly manufactured engines under various mechanical loads. This is accomplished by connecting the engine to the load bank via a device called a dynamometer. Again, engine performance is monitored and, if necessary, adjustments are made to ensure the product performs within intended specifications
Contact Person: Bruce