Payment & Shipping Terms:
|Rating Voltage/Frequency:||440VAC/50Hz, 3 Phase 4 Wire||Casing Color:||Grey（RAL7035）|
|Weight:||5000kg||Data Processing Software:||Kaixiang（self-developed）|
|PF:||0.8-1||Max Rated Power:||Apparent Power:1375KVA Resistive Power: 1100kW Reactive Power: 825kvar|
Professional Design And Produce 400V 1375KVA Inductive Load Bank
A load bank is an electrical apparatus used to verify the performance of an electrical power source. The most common application for the equipment is to provide an exercise "load" for standby emergency generators. These emergency generators are typically installed at hospitals, hotels, office buildings, skyscrapers, water treatment facilities, data centers, large retail facilities, and other such sites
|Rating Voltage/Frequency||440VAC/50Hz, 3 phase 4 wire|
|Max Rated power||
Resistive Power: 1100kW
Reactive Power: 825kvar
Resistive Load: 0.5.1.2.126.96.36.199.188.8.131.52.184.108.40.206KW
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
|Casing Dimensions and Cooling||Forced air cooling,Horizontal inlet air,Vertical cooling|
1. High Efficiency Data Management: display real-time testing data, generate form, curve graph or report automatically, also can put data into storage. According to generator set No. set up testing file, support to query at any time, and improve data management efficiency.
2. Comprehensive Protection Function: multiple protection, like over temperature, smoke. When in danger, automatically terminate the test and give alarm to protect safety of personnel and equipment.
3. Stable Running: with the latest generation control module as the core, a sharp rise in system response speed and anti-interference performance, avoid function failure in complex electrical environment, and ensure system running stably and reliably
Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce