Payment & Shipping Terms:
|Resistive Load:||100KW*1.200KW*2.500KW*1.1000KW.2000KW||Rated Power:||Copper Bar (star Coupling) 50MW Connector-bar 54MW|
|Load Tolerance (overall):||±3%||Size:||8950*2438*2591mm|
|Weight:||19000 KG||Display Precision:||0.5 Class|
High Voltage Capacitor Tester 10.56KV 3KV 50MW Medium Voltage Load Bank
load banks are devices which contain resistive,inductive and/or capacitive loads,apply the load to an electrical power source and dissipate the power of the electrical source .unlike the on-site loads which are randomly variable in terms of many electrical parameters ,load banks provide predetermines and controllable load which serves power source usings energy output to test,support or protect the power source
|Rating Voltage/Frequency||10.5kV/50Hz, 3 phase 3 wire|
Copper bar (star coupling) 50MW
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
Load power supply input——Copper bar (star coupling)
Control power supply input——Connector-bar
Communication Mode:RS485/ USB or RS232 interface for communication.
Load Mode: manual load or automatic load. It has three control ways for customer choose.
Manual Load: input power and power factor, and load according to the preset value.
Automatic Load: set several load stages and duration, then complete the process according this stages automatically. 0%- 25%,- 50%,- 75%, -100%
Real-time Monitor: through software display main parameter value, such as voltage, current, power, power factor, frequency and time.
Motor manufacturing: The load bank is an ideal test equipment for generator power ,the frequency,the voltage,the current,power factor and other generator parameters.Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load.
Contact Person: Bruce