Payment & Shipping Terms:
|Max Rated Power:||Apparent Power: 19700kVA Resistive Power: 500kW Reactive Power: 375kvar||Rated Power Facor:||0.8|
|Casing Dimensions And Cooling:||About 1540*1250*1680mm (length*width*height) Forced Air Cooling，Horizontal Inlet Air，Vertical Cooling||Transportation:||Hoisting, There Are Lifting Lug In Top Of Casing|
|Casing Color:||Grey（RAL7035）||Ambient Temperature:||-10℃～+50℃|
High Quality Good Price 400V 625KVA Inductive Load Bank For Middle East
The system consists of 1 sets of AC400-625kVA-RL load bank. The system is made up of two parts of measurement and control and load, mainly including the tank dry type ac load, automatic data acquisition system, automatically loading and unloading control system, the cooling device, auxiliary control, remote control box and PC software and so on.
|Rating Voltage/Frequency||400VAC/50Hz, 3 phase 4 wire,|
|Max Rated power||
Apparent Power: 19700kVA
Resistive Load: 184.108.40.206.10.10.20.50.100.100.200kw
|Load Tolerance (each step)||±5%|
|Display Precision||0.5 class|
Load power supply input——Copper bar (star coupling)
|Casing Dimensions and Cooling||about 1540*1250*1680mm (length*width*height) Forced air cooling,Horizontal inlet air,Vertical cooling|
|Transportation||Hoisting, there are lifting lug in top of casing|
|Data processing software||Kaixiang(self-developed)|
Kaixiang company is in leading position in generator set testing and maintenance industry, besides general functions, its load bank has following unique advantages:
1. Intelligent Load: after setting generator rated power in software, system realize rapid loading through preset proportion, automatically and continuously load multiple power value and common tests, like stepping, full load, and over load, so that improve working efficiency.
2. High Efficiency Data Management: display real-time testing data, generate form, curve graph or report automatically, also can put data into storage. According to generator set No. set up testing file, support to query at any time, and improve data management efficiency.
Most of the generator use the diesel oil,which can cause the fuel oil unfilled,carbon deposition ,complete machine efficiency reduced when the diesel oil load is lower than 50% or in idling situation for a long time and even cause starting difficulty ,power insuffciency,oil consumption increased,finally,opening the cylinder for maintenance too early and the abandonment ,so the load bank will be generator's ideal false load
Contact Person: Bruce